Quiz: Electrical Engineering
Each question carries 1 mark.
Negative marking: 1/4 mark
Time: 10 Minute
Q1. If the secondary winding of the ideal transformer shown below has 40 turns, the number of turns in the primary winding for maximum power transfer to the 2 Ω resistor will be:
Q2. Parallel branch elements can be found out in a 1-phase transformer by conducting
(a) Open circuit test
(b) Short circuit test
(c) Both SC and OC test
(d) None of the above
Q3. 100 % string efficiency means
(a) Zero potential across each disc
(b) One of the insulator discs shorted
(c) Equal potential across each insulator disc
(d) None of the above
Q4. What is the approximate efficiency of a normal thermal power station?
(a) 20-25 %
(b) 30-40 %
(c) 45-55 %
(d) 60-70 %
Q5. To minimize the current chopping tendency, the SF6 gas is used at
(a) Low velocity and low pressure
(b) High velocity and high pressure
(c) Low velocity and high pressure
(d) High velocity and low pressure
Q6. The equivalent resistance in ohms in the circuit shown is
Q7. If r is the radius of the conductor and R is the radius of the sheath of the cable, the cable operates stably from the point of view of dielectric strength if:
(b) r/R<1 (c) r/R<0.368 (d) r/R>2.718
Q8. As per Indian Electricity rule in overhead systems, the recommended span in case of RCC pole is….
(a) 40-50 meters
(b) 50-80 meters
(c) 80-100 meters
(d) 100-300 meters
Q9. Which lightning stroke is most dangerous?
(a) Direct stroke on the line conductor
(b) Direct stroke on the conductor
(c) Direct stroke on the ground wire
(d) Direct stroke on the tower top
Q10. Voltage regulation due to the Ferranti effect may be:
(d) All of the above
Sol. For maximum transfer to the 2 Ω resistor:
Sol. For determining shunt branch elements (Rc,xm), we perform OC test at rated voltage.
Sol. Due to formation of stray capacitance, unequal potential distribution occurs across discs which is expressed in terms of string efficiency.
If the string efficiency is 100 % then it means that equal potential difference occurs across each insulator disc.
Sol. Efficiency of a normal thermal power station≃ 30-40 %.
Sol. Due to low velocity and pressure employed in SF6 CBs, current chopping is prevented and capacitive currents are interrupted without restriking.
Sol. Geff=(G1×G2)/(G1+G2 )=(2×4)/(2+4)=8/6
Req = 1/Geff =6/8=3/4 Ω.
Sol. The cable operates stably from the point of view of dielectric strength if:
R/r>e or 2.718
∴r/R<1/e or 0.368
Sol. RCC poles: span=80-100 meters
|Line support||Recommended span|
|Wooden pole||40-50 meters|
|Steel pole||50-80 meters|
|RCC pole||80-100 meters|
|Steel tower||300 meters or above|
Sol. In this case, high voltage surges will damage the equipment.
Sol. Voltage regulation: (VS-VR)/VR
Due to Ferranti effect: V_S<V_R
Hence, voltage regulation is negative in case of Ferranti effect.